Home > Offers to Sell > Home Appliances > Air Cooling, Purifying & Humidifying > Air Conditioners
||Zhejiang Aoshuai Refrigeration Co., Ltd
||3-1-3, Cantonment Exchange, 698, Jalan Sultan Azlan Shah (Jalan
||12/14/21 2:50 GMT
Cooling Tower Gearbox
As an industrial cooling towers LLC, AUVC can provide different types of
cooling tower parts. Using high-quality raw material which is the same as
liangchi, marley, bac, kuken, kingsun.
The gear reducer is designed as a kind of reduction equipment of a cooling
tower, which is generally used for transmission equipment with low speed and
large torque. It uses all levels of gear transmission to achieve the purpose of
speed reduction. The gear is made of high strength low carbon alloy steel by
carburizing and quenching, and it is widely used in metallurgy, mining,
lifting, transportation, cement, construction, chemical industry, textile,
printing, dyeing, pharmaceutical, and other fields.
As one of the professional cooling tower gearbox manufacturer, we provide
different types of cooling tower gearbox parts, such as gearboxes. You can
select what you need from the different types of cooling tower gearbox
repair/cooling tower gearbox type.
Precautions for Cooling Tower Gearbox Assembly
a. Before installation of the cooling tower fan gearbox, check whether the
matching of the reducer and fan meets the cooling tower gearbox design
requirements. Generally, the reducer should be hoisted as a whole. If it is
hoisted separately, attention should be paid to that the steel ball in the
taper hole of the main shaft should not be missed or displaced, otherwise the
parts will be damaged.
b. Generally, 10-15mm thick rubber pad should be added between the reducer and
mounting frame to reduce vibration.
c. After installation of the cooling tower fan gearbox, check that the
clearance between the fan blade and the tower body should be uniform, and the
reducer should be turned by hand. The fan should rotate flexibly without
clamping, otherwise, it cannot be powered on.
d. Oil must be added before operating the cooling tower gearbox oil, special
gear oil should be added. When adding oil, it should be introduced from the oil
pipe. After adding oil, the oil level should reach the middle line, and then
the oil needle should be tightly covered. The cooling tower gearbox maintenance
is equipped with an oil mark, oil filling and discharging pipeline and ball
valve, which can check the oil level without stopping the machine and refuel in
The Gear Reducer of Cooling Tower Has the Following Characteristics
a. High transmission efficiency, energy saving: planetary transmission
principle design, and high manufacturing accuracy, transmission efficiency of
more than 97%.
b. Low noise: high gear grinding accuracy: the internal design of the reducer
has noise isolation structure, so that the noise of the reducer can be
controlled to meet the needs of low noise cooling tower.
c. Beautiful appearance and small volume: the motor and reducer are driven by
the whole coaxial line, with beautiful appearance. The structure design is
d. Good sealing performance and stable performance: different sealing methods
are adopted to make the lubricating oil not easy to leak. The gear is made of
alloy steel with large bearing capacity and good stability.
Minimum Order: 1 gallons
Click to Enlarge
SOURCE: Import-Export Bulletin Board (https://www.imexbb.com/)
Post an Offer to Sell
© 1996-2010 IMEXBB.com. All rights reserved.